Air Conditioning, Heating & Plumbing in Chandler, AZ
You can always rely on Hobaica Services for home comfort. We provide professional service for residential air conditioning, heating and plumbing in Chandler, AZ. Call Hobaica at (602) 633-9555 for quality services from a company dedicated to your satisfaction.
Learn more about the services we offer:
Check out some of the reviews we’ve received from Chandler, AZ residents below. See why our customers are repeatedly satisfied with our work.
for Chandler, AZ
Katrina - Chandler, AZ
Tony - Chandler, AZ
Jeanne - Chandler, AZ
Timely, knowledgeable, professional, personable, and inexpensive for services provided. Can nott get any better than that!
Shuchin - Chandler, AZ
Tom is really a hard worker! He was honest, knowledgeable and very helpful. I will definitely use him again in the future.
great service, friendly & professional technician!
Cheryl - Chandler, AZ
The only thing I struggle with is the time window you give us to be here for the tech. Four hours is four hours of valuable time for me, as well. I don't know that I want to race home to be here by 12 noon (& miss work), to sit here till 3pm when your tech shows up. Not sure what I'll do for the next appointment.
Shirley - Chandler, AZ
Great service and very informative
Barb - Chandler, AZ
From scheduling to actual service excellent!
Great Service, Very Thorough
Bruce - Chandler, AZ
tom is very respectful and does his job quickly and well.
Dale - Chandler, AZ
Good fellow. Will ask for him again.
Plumbing service was excellent and market priced.
Gary - Chandler, AZ
While the original service technician was unable to leave the job he was assigned before me, Hobaica phoned and notified that Thomas, another experienced technician was en-route to provide the service required. Thomas was friendly, courteous, and professional with a well stocked service van. Problem corrected in about an hour.
Perform diagnostic on a Lennox split heat pump system.
Cut in a new 14” return and new 10” supply in the master bedroom
Install new split ac
Recently went out on 12/1 for scheduled maintenance, customer is stating his outside unit is continously turning on out of nowhere then runs for a few mins than shuts off again for several minutes then starts back up. Chris said hes not sure why its turning on because his thermostat is telling him its the correct temperature, it shouldnt need to turn on. he seems pretty informed about his unit, he said it sure its not in defrost cycle. he also turned off his thermostat and unit is still turning on and off.
Completed service gas split system. Cycle system on heat/cool and checked refrigerant pressure electrical motors bearing amp draws run cap sequence of operation on gas furnace. Found system Note2: is operational ok in both heat and cool mode. Discussed with customer about filter and he said he has been order filter online. N
Perform thermostat diagnostic.
was explaining to me that when the unit is cooling she can smell heat and the unit blows warm air at the beginning and end of each cooling cycle. Like the furnace is on at the beginning and end. She said she can smell it every time. I went up to the attic and cycled the unit on and off of cooling cycles ten times and the furnace never came on. I did find that the blower delay was on for 240sec so I adjusted it to 90 sec. I did notice some oil stains in secondary pan. I check refrigerant
Perform biannual service on a gas split system. Cycle system on cooling and checked refrigerant pressure, electrical, motors bearing, amp draws, run caps, and operational. Found condensate drain line was clogged and causing overflow. Flushed out drain line and noted drain pan did not level. Level drain pan and installed blow out valve. System is operational ok at this
Perform bi annual service for Lennox split heat pump system.
Check out the Trane clean effect.
2005 #r22 split heat pump in attic and on roof. R22 pressures are low and compressor contactor switch is wearing out, there are also no condensate safeties in attic, could be added in spring or with new system. Recommended new system at this time due to possible r22 leak and overall age and condition.
Performed pcp maintenance in cooling. Checked air filter and changed with customer supplied expandable filter, checked thermostat, coils, electrical, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, blew out condensate drain line with nitro and rinsed outdoor coil with water. System is operating normally and readi
Perform bi annual service for a Lennox split heat pump system.