Air Conditioning, Heating & Plumbing in Phoenix, AZ
Since 1952, the Phoenix, AZ air conditioning and heating experts at Hobaica Services have been providing comfort to our valued customers. We now offer plumbing services as well! Call us today at (602) 633-9555 if you need repairs, installation or maintenance for your home’s air conditioning, heating or plumbing in Phoenix, AZ.
We are able to provide services for all your home comfort needs:
Read our reviews below to see why our customers in Phoenix, AZ are pleased with our outstanding work. Our focus on amazing service and customer satisfaction is the reason we continue to receive 5 star service ratings again and again.
An AC repair in Phoenix typically costs anywhere from $100 - 900. The cost can go lower than this for very minor repairs, or it could go up to as much as $2,000 for more serious repair needs.
The best way to know how much your AC repair will cost is by getting in touch with a professional AC contractor who can provide a free estimate. Call (602) 633-9555.
If your AC is not blowing cold air, check your air filter. A dirty air filter is the most common cause of a lack of cool air from your system. Other causes include low refrigerant and a clogged outdoor unit. If you want to know for sure what the cause is, get in touch with Hobaica Services for a free quote or call (602) 633-9555.
The cost of a new AC unit in Phoenix is really going to vary depending on what type of AC you get installed, what extra materials you need to have it installed and which contractor you choose for the installation. It could cost anywhere from $4,000 - $25,000.
For reasonable AC replacement estimates in the Phoenix area, get in touch with Hobaica services. Call (602) 633-9555.
Your sink may back up when you run your garbage disposal because your drain lines are clogged. Fortunately, you should be able to address this problem easily by filling your sink partly with water and using a sink plunger to unclog the drain. However, if you are unable to clear the drain line with the plunger, you may need to implement an alternative method. If you are unable to unclog your drain yourself, you can also have a plumber unclog it for you. To get your drain unclogged, give us a call today.
Some symptoms of bad air quality in your Phoenix area home include:
- Headache, fatigue or nausea.
- Dry throat, skin, eyes or nose.
- Increased allergic reactions.
One of the biggest signs that you have poor indoor air quality in your home is if you feel worse at home than when you’re out and about. Increased allergic reactions is one of the biggest signs that your indoor air quality is poor and needs to be addressed. To get your indoor air quality improved, contact us today.
To choose a good electrician in Phoenix, AZ you should:
- Ask coworkers and friends for recommendations.
- Check customer reviews online.
- Ask electricians for references.
Another thing you should also check before choosing an electrician is if they are licensed and insured. An electrician that is properly licensed and insured will be able to do the job correctly and to electrical code. To learn about our electrical services, call us today.
for Phoenix, AZ
Another outstanding service visit from Hobaica
Edward - Phoenix, AZ
Service call from Hobaica’s John Miranda earlier this week was yet another outstanding encounter. This very knowledgeable young man was so professional and once more proved how well the employees of this unparalleled company perform their duties. Thank you John for a job well done. ENA
Service on our home furnace
Abel - Phoenix, AZ
Binh was here to replace the gas valve on our home furnace. His efficiency and expertise is always appreciated.
We have heat again. 🙂
Steve - Phoenix, AZ
Tom performed the initial diagnosis, had the parts ordered and then completed the repair. Everything went just as he described, and in the time frame he laid out. Happy wife = happy life. Thanks Hobaica!
Judy - Phoenix, AZ
Ken - Phoenix, AZ
Ian was knowledgeable and timely.
Mike - Phoenix, AZ
John Miranda was awesome. Very professional and informative.
Nick - Phoenix, AZ
My service was excellent and the sent out to help me was personable and explained everything.
Jill - Phoenix, AZ
Hobaica has been my go to HVAC company now for 10 years. Service is always phenomenal and today was no exception. My technician Travis was friendly and thorough in explaining the suggested repairs. Jordan was equally friendly and together they left my house the way they found it. Great job guys!
Tina - Phoenix, AZ
Neat, timely & great service
Nelson - Phoenix, AZ
Shower fixture repair
Judy - Phoenix, AZ
Travis was very thorough and checked the cartridge in the fixture to make sure it did not need replacement. He was very professional and friendly.
Fast, friendly maintenance
Bob - Phoenix, AZ
Ian was fast, friendly, and efficient.
Malia - Phoenix, AZ
I had a wonderful experience with technician John Miranda. He was thorough and very friendly and helpful with advice.
Henry - Phoenix, AZ
Job well done.
Kristina - Phoenix, AZ
Binh was a pleasure to work with. He knew to not rest a ladder on my metal roof, which not all bother to pay attention to.
Diana - Phoenix, AZ
Ian was very professional and gave me good advice concerning my air conditioning units. I continue to use hobaica due to the quality of work that they perform.
Suzanne - Phoenix, AZ
Ian was helpful with my questions, careful not to get my floor dirty, took his time to complete his assessment of my AC unit, and was thorough with the maintenance service. Great job.
Bechara - Phoenix, AZ
Ian was courteous, professional, and on time.
Mary - Phoenix, AZ
He quickly determined our problem and fixed it.
Hobaica is good
Sandra Thomson - Phoenix, AZ
Ian was helpful
Great customer service and attitude
Tom - Phoenix, AZ
Ian Flood was on time, polite and professional. I would be pleased if he was our service technician for our next service.
We always receive great service from all of the Hobaica technicians.
Bob - Phoenix, AZ
James - Phoenix, AZ
Keith - Phoenix, AZ
This was our semi annual service call. They were professional in every way.
Catherine - Phoenix, AZ
John Miranda was so pleasant, thorough, and informative when he came to do my routine maintenance. Made me feel confident that my HVAC unit will work well for the season, and if there is any problem Hobaica will be right here to fix it. Thank you so much!
Complimentary second opinion on drain line
Performed OEM indoor blower motor and control module replacement on 1 Daikin Package Heat Pump Unit.
Warranty first year
Warranty first year
Replace gas valve
Performed biannual service
Oem piston from daiken sent was 072 and the one I removed is 059. I replace the outdoor piston as well as the liquid line filter located inside the condenser while flowing nitrogen after recovering all of the refrigerant charge. I pressure tested and leak checked and then evacuated system below 500 µm and recharged with 115 ounces of new r410a. Compressor amps 8.8. Pressures 112/320 SC 6. Outdoor ambient 68. System is back online heating properly now.
Maintenance on a Trane furnace
I found System locked out on high pressure. I set defrost timer to run longer between cycles and increased heating fan speed to high. Liquid line pressure is getting a little high at about 515. Temp rise is high 80/120. Static pressure is low at total .25 and amp draw of the blower motor is low at 1 Amp. I suspect we need to replace the blower motor, Office will follow up
Maintenance on a daikin gas pack
Core sense locked system out on pressure switch cycles, Outdoor piston metering device is restricted and needs replaced. It is causing low pressure switch to open. Pressures in heating 54/254 SC 15. I cycled in cooling to make sure refrigerant pressures are ok, 110/216 SH 20, SC 8.
Electrical connections Amp draws Capacitors Motors Bearing wear Coil condition Controls Thermostat operation Temperature split Static pressures Air filter Cleared condensate drain line Duct seal at unit Refrigerant pressures The unit is in the sunset of its life and has been for some time, today I noted that the unit should be retired and replaced with a new more efficient unit, it does not make sense to repair this unit any longer, I recommend saving the money and putting it towards a new
Performing TCC maintenance on 1 package heat pump. Testing unit in heating for winter.
Downtown Phoenix, North/Northwest Phoenix, South Mountain Village, Camelback East, North Mountain, Central City, Phoenix, Desert Ridge, Norterra, Cavco, Arcadia Cove, Pointe Tapatio, West Phoenix, Campus For Compassion, Canyon Creek Village, Optima Biltmore Towers Condominium, Papago Vista Apartments, Desert West Park, Lookout Mountain Preserve, Biltmore Area, Little Dealer Little Prices, Mountain Park Ranch, Arizona Biltmore Estates, Phoenician, Sonoran Foothills, villagio at happy valley, Tatum Ranch, Villa De Paz, Cofco Chinese Cultural Center, Arcadia Lite, Indigo Palms, Crossroads West, Monterey Ridge Condominium, Adobe Ridge Apartments, Pointe Resort Condo At Tapatio Cliffs, Raven At South Mountain, Cave Creek Transfer Station, Colonia Del Sol, Courtney Village At Papago Park, Evans Churchill, Discovery At Villa De Paz, Khalsa Montessori, Paradise Park Condominiums, Paseo Pointe, Pierson Place Historic District, Paradise Valley Oasis, Arcadia Residences Condominium, Anasazi Village Condo, Mountain Park Condominiums, Enclave Villas Condominium, Stetson Valley, Woodlake Condos