Hobaica is proud to provide the residents of Apache Junction, AZ with expert air conditioning, heating, electrical, plumbing & sewers and drains services. Our family-owned and operated local business has been serving your area since 1952 with exceptional work and friendly service.
We invite you to read some of our reviews below and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Apache Junction, AZ.
for Apache Junction, AZ
Our Reviews by City
Maintenance check up
AJ - Apache Junction, AZ
Scott was our service technician assigned to do our “6 month check up” on the AC and furnace. He was very thorough and very courteous. Reassured us that all is well going into the hot summer here in Arizona. Went above and beyond to make sure all my questions and concerns were answered. He also changed out several of our smoke alarm batteries which was very much appreciated. Hobaica always calls to remind me when we are due for our 6 month check up. I also appreciate the communication that Hobaica provides regarding not only the name but also a picture of the technician that will be arriving. Thank you!
Joe - Apache Junction, AZ
Fast diagnosis, courteous, friendly. I would like Anthony to work on all my homes and rentals.
Tcc Silver Maintenance
Tcc bronze maintenance
Perform bi annual services.
Danny U. Performed seasonal maintenance on Sam and Karen’s Daiken heat pump. Here is the review link. A 5 star google review is the best type I can receive. You need a Gmail account though. Any 5 star review with my name being mentioned will make my day! Thank you for your time Sam. Semper Fi!
Follow up to replace indoor coil under manufacture part warranty. Recovered refrigerant from system. Removed and replaced indoor coil, biflow drier. Pressurized system to 300 PSI and checked for all connection made. Evacuated system down to 500 microns. Weight in 5lbs 13oz of fresh R410A. Cycled system on cooling and found system pressure 110/300 PSI. Supply air temp 50 and return 73 degrees. Cycled system on heating and found
blower motor, airflow, temp rise and system is all operating normally and within manufacture specifications at this time, ready for winter. Also performed whole house plumbing inspection, water heater in backyard has small amount of rust on hot water outlet, it is dry and ok now. 3 bathrooms, kitchen, laundry, water stops and supply hoses all ok. thank your for your continued confidence.
Perform service on a Rheem package heat pump system.
Perform service or both gas split systems.
Arrived in Gold canyon to perform a diagnostic service on a Lennox A/c with gas system. Rewired condensation pump. Tested condensate pump operation as well as condensate safety switch. Thank you very much for choosing Hobaica services. Have a wonderful day.
Parkwood Ranch, Deer Valley, Anthem at Merrill Ranch, Signal Butte Ranch, Pioneer Estates II, Desert Sands East, Rancho Cimarron, Arroyo Verde, Superstition Springs, Sunland Springs Village, Fountain of the Sun, Sunland Village East, Alta Mesa Community Association, Sundance Homes, 2nd Ave. Group, MGM Neighborhood, Alta Mesa Estates HOA, Reed Park Neighborhood, Speedway Neighborhood, Dobson Ranch