Hobaica is proud to provide the residents of Apache Junction, AZ with expert air conditioning, heating, electrical, plumbing & sewers and drains services. Our family-owned and operated local business has been serving your area since 1952 with exceptional work and friendly service.
We invite you to read some of our reviews below and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Apache Junction, AZ.
for Apache Junction, AZ
Our Reviews by City
Joe - Apache Junction, AZ
Fast diagnosis, courteous, friendly. I would like Anthony to work on all my homes and rentals.
Danny U. Performed seasonal maintenance on Sam and Karen’s Daiken heat pump. Here is the review link. A 5 star google review is the best type I can receive. You need a Gmail account though. Any 5 star review with my name being mentioned will make my day! Thank you for your time Sam. Semper Fi!
Follow up to replace indoor coil under manufacture part warranty. Recovered refrigerant from system. Removed and replaced indoor coil, biflow drier. Pressurized system to 300 PSI and checked for all connection made. Evacuated system down to 500 microns. Weight in 5lbs 13oz of fresh R410A. Cycled system on cooling and found system pressure 110/300 PSI. Supply air temp 50 and return 73 degrees. Cycled system on heating and found
blower motor, airflow, temp rise and system is all operating normally and within manufacture specifications at this time, ready for winter. Also performed whole house plumbing inspection, water heater in backyard has small amount of rust on hot water outlet, it is dry and ok now. 3 bathrooms, kitchen, laundry, water stops and supply hoses all ok. thank your for your continued confidence.
Perform service on a Rheem package heat pump system.
Perform service or both gas split systems.
Arrived in Gold canyon to perform a diagnostic service on a Lennox A/c with gas system. Rewired condensation pump. Tested condensate pump operation as well as condensate safety switch. Thank you very much for choosing Hobaica services. Have a wonderful day.
Residential preventative maintenance tune up AC, air handler and evaporator coil. Clean condenser coil and condensate drain line, check duct static pressure, airflow, refrigerant pressures, temperature split, air filter, compressor, motors and fans for best efficiency. Inspect air conditioner, capacitor, contactor, safeties, electrical, thank you for your continued confidence in our HVAC, wine cellar, and home performance energy audit services.