Air Conditioning, Heating & Plumbing in Phoenix, AZ
Since 1952, the Phoenix, AZ air conditioning and heating experts at Hobaica Services have been providing comfort to our valued customers. We now offer plumbing services as well! Call us today at (602) 633-9555 if you need repairs, installation or maintenance for your home’s air conditioning, heating or plumbing in Phoenix, AZ.
We are able to provide services for all your home comfort needs:
Read our reviews below to see why our customers in Phoenix, AZ are pleased with our outstanding work. Our focus on amazing service and customer satisfaction is the reason we continue to receive 5 star service ratings again and again.
for Phoenix, AZ
Justin saved me on two services...
Claude - Phoenix, AZ
I’ve known about Hobaica for many years but I didn’t realize they actually did HVAC repair. So I give them a call. I was able to set up a time and appointment that worked for my schedule. Justin was the technician. Justin came out and got to work right away. When the work was finished Justin sat down and talked to me about the repairs he did. He also mentioned about their silver plan repair program. In doing so I was able to save quite a bit of money on current service that Justin performed. On the same day I also had another Hobaica technician service another house at mine. The technician did a good job, but just did not mention about the service plan available. I was able to call on Monday or Tuesday as a follow-up and I spoke with Noah. I explained to Noah about getting the service plan on my other property. He too was able to save me money on the second house AC repairs. Way to go Justin and Noah and thank you Hobaica!!
Hobaica Services...What a Great Customer Experience!
John - Phoenix, AZ
Binh Tran (Hobaica Services) serviced my A/C units. He really is an ambassador for Hobaica, in addition to being a Service Expert. It is gratifying to have found a service company worthy of trust. Hobaica is my go-to company for my future A/C and plumbing needs, as of today. Thank you for your honesty, professionalism, and excellent customer care.
PHX Greenthumb - Phoenix, AZ
Very Professional, knew what he was doing. Friendly. On my service by him only list.
"Great Service, Awesome Price!"
Michael - Phoenix, AZ
Appointment day after I called.Justin was great. Friendly, professional, and no BS.
Awesome Customer Experience
Rene - Phoenix, AZ
Everything from beginning to end was an awesome customer experience!
Michael - Phoenix, AZ
Isaiah was very pleasant & professional. Excellent service.
Maria - Phoenix, AZ
Our dishwasher was installed without any glitches. Terrill was very friendly and helpful! I'd definitely recommend Hobaica to a friend!
Ricky Bobby Speeds
Rotten Tomato - Phoenix, AZ
Excellent service and speedy response
eat professional and pleasant service
Chuck - Phoenix, AZ
Duncan - Phoenix, AZ
Performed maintenance on a trane package heat pump. Changed filter and checked thermostat operations, checked return and supply temperatures and static pressures, checked compressor operations and refrigerant pressures, checked compressor amps and outdoor motor amps and indoor motor amps, checked capacitors and tightened all electrical components, indoor coil is clean and outdoor coil is clean and drain line/pan is clear. U
Training w Ronnie
Training day with Lou
Perform Hobaica special service.
Call fo not enough hot water. Water heater lower element was not coming on due to bad lower thermostat, we can replace one or proactively replace both thermostat today. David approved to replace just the lower water heater thermostat today, I did and tested out hot water, all operating properly now. Each element pulls 18A.
Perform maintenance on a Daikin package heat pump. Checked filter, thermostat operation, return and supply temperature, refrigerant pressure, compressor, indoor and outdoor motor amps, capacitor, tightened electrical connections, indoor and outdoor coil, drain pan/line is clear. Unit is running properly at this time.
Perform Hobaica special tune up.
2017 nortek condensor I found off on high pressure fault. Capacitors test ok. I found outdoor fan motor was overheated, still hot and off on internal protection. Outdoor fan motor should be replaced with oem. System is off outside to protect compressor from burning out. Went over tcc plans. Office can check part warranty in AM during regular hours and will call back customer. Customer is not original equipment owner.
erformed split heat pump maintenance in cooling. Checked air filter, thermostat, coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line with water. System is operating normally and readings are within manufacture specifications at this time. Thank you for your continued confidence. Went over tcc and labor warranty plans, time to renew
Performed maintenance service on a daikin split heat pump. Evaluated in heating. Checked filter temperature split static pressures refrigerant pressures amp draw coils controls motors condensate drain/safety electrical connections and disconnects. I tightened electrical connections. All read are within manufacturing specifications on today’s visit. Discussed and recommended a surge protect
System does use #r22 refrigerant that is due to end production this year, it would be a good idea to start planning on upgrading equipment soon with new more efficient unit. Thank you for your continued confidence. Went over tcc plans, $15.99 monthly price for heat pump over 10 years.
Took pic of how line set cover was at arrival and I secured line set cover for customer. Made sure cover is not going anywhere now with screw at bottom of cover, by condensate pvc drain, behind mini slit condenser. Also sealed top of cover at elbow with clear silicone, and took video of repair.
Perform diagnostic for basement system,
Replace angle stop
Replace angle stop
Perform special tune up for a split heat pump system.
Residential hvac service north valley
replaced 4L510 belt. At arrival found evap cooler out of water, pump and blower where still running. customers report they turned off valve near hose bib because it was leaking on ground outside from Around the valve and 1/4 inch compression tee, I tightened up fittings and got leak to slow to tiny drip every 13-15 seconds instead of steady stream like before. Left water turned back on. Dripping outside of home. 1/4 inch m.i.p compression valve needed to fully stop leak as well as 1/4 inch.
I noticed outdoor fan motor bearings are beginning to drag and outdoor fan motor likely will overheat in coming months and then the new compressor will also overheat. 1/3 hp 1075 rpm outdoor fan motor should be replaced now proactively before this happens or system will be down again. As of now system is operating properly again.
Toilet issues. Found flapper does not re-seat correctly and toilet continually runs, noticed fill valve is plugged and very slow to fill. Also noticed angle stop is old and feels frozen, likely to leak if it’s used. I bent rod to handle and flapper seats better now. Recommend major toilet rebuild, remove tank and replace seals and the flapper and fill valve and also should replace the angle stop. Customers approved to return and install Hobaica supplied standard round toilet.
Performed maintenance on one split heat pump in heating. Changed filter customer supplied. Verfied operations, pressures, amp draws, capacitors, motors and coils. Found contactor has slight pitting we will monitor next visit. System is functioning properly with no further issues to report at this time. Thanks for choosing Hobaica
Performed spring evaporative cooler maintenance and stat up, turned on water and rinsed out reservoir. Checked drain and for leaks and fill level. Checked set screws and bearings. Checked cooler pad, blower belt and pumps. Turned on power and tested out cooler. It is in good shape and operating properly at this time.
Performed inspection on 2 ceiling mount straight cool split systems. Cleaned filters, verified operations, pressures, amp draws, capacitors, motors and over all conditions. Both units are functioning at this time. I went over age of units and r2w refrigerant phase out. I do not recommend making any repairs on these units going forward I would replace them. Recommend customer begin planning for replacement no guarantee how long these units will continue to function.
Recovered old leaking r410a charge, removed old coil and welded in new coil. vacuum pumped system to remove moisture, down to 300 microns and held, pressure tested to 175 psi with nitro and leak checked and recharged with 8 lbs new r410a. Tested system in cooling. Condenser XP14-024-230-07 Serial #5811B19915 airhandler CBX27UH-024-230-6-02 Serial #5810M13171. Call complete, system is operating properly now. Customer left behind $75 off in Hobaica gift cards, I applied discount today.
Did maintenance on one Lennox gas pack, checked motor amp draws, checked run capacitors, inspected coils, checked refrigerant pressures, checked static pressures, cycled system in heating, checked ignition sequence, flame looks good, indoor blower cycles normal, did full combustion analysis. System is working good