Air Conditioning, Heating & Plumbing in Phoenix, AZ
Since 1952, the Phoenix, AZ air conditioning and heating experts at Hobaica Services have been providing comfort to our valued customers. We now offer plumbing services as well! Call us today at (602) 633-9555 if you need repairs, installation or maintenance for your home’s air conditioning, heating or plumbing in Phoenix, AZ.
We are able to provide services for all your home comfort needs:
Read our reviews below to see why our customers in Phoenix, AZ are pleased with our outstanding work. Our focus on amazing service and customer satisfaction is the reason we continue to receive 5 star service ratings again and again.
for Phoenix, AZ
Ron is great
Lyn - Phoenix, AZ
On time, left no mess and very informative
Julie D. - Phoenix, AZ
Justin called before he came. He was so quiet we thought he had left but he was just out in his truck. Very polite and informative about our A/C units.
A True Service-Man
Camille - Phoenix, AZ
Tom is oriented toward customer service which he does with a smile. This courteous, friendly man is most welcome to return anytime I need Hobaica service.
Super great service and Steve Avila was professional-timely-and worked clean
Anna - Phoenix, AZ
I recommend Hobaica!
Alan - Phoenix, AZ
Appreciate the Custom Service
Mike - Phoenix, AZ
Very pleasant and easy to relate with. Crappy situation, friendly service
Carol - Phoenix, AZ
Steven went above and beyond on the appointment. I will request him on my next visit.
Buster01 - Phoenix, AZ
Hobaica Services scheduled a technician to address an issue with my air-conditioning unit over the weekend. They said they would be between 11:00AM and 4:00PM. Ron called me before shortly after I scheduled the appointment and said he would be there within the hour. Outstanding, it was going to be hot day and the AC wasn't operating properly. Ron was professional, courteous, polite and knowledgeable. He quickly identified the problem, effected repairs and returned the unit to service. The charge for the visit was very reasonable. Thank you very much Ron, it was a pleasure. I highly recommend Hobacia and will use them in the future.
Tankless water heater
Tim - Phoenix, AZ
Outstanding Service, Very Professional
Geraldine - Phoenix, AZ
Today I had the need for A/C repair. Ken B. from Hobaica Services came to check out the problem. Ken had our A/C repaired within a very short amount of time. He looked at the unit, asked a few questions, and diagnosed the problem right away. Fortunately the issue was resolved with technical service and no parts were required. What a relief!! Ken patiently explained the problem that he encountered and what the solution would be. Ken has many years of experience that allows him to quickly diagnose and fix the problem. Would recommend Ken B and Hocaica Services for all you A/C issues.
Found failed compressor capacitor, reading 0 and exploded. Compressor only started because of aftermarket start assist is installed. Recommended heavy duty Capacitor with its own warranty, I Repalced 80/10 mfd run capacitor with standard cap and customers approval under parts only. Time to renew tcc plan and I went over pricing and sent info. I left a spare truck stock 20x30x1 filter and changed with customer supplied.
Performed previously approved repair of replacing seized condenser fan motor. Installed new motor and tested operations. The system is now cooling well. Thank you very much for choosing Hobaica services. Have a great day.
Performed a residential service inspection Phoenix on a split unit that is not cooling. Identified fan motor is bad. Owner approved repair. Thank you for choosing Hobaica services. Have a great day.
Kitchen furnace LENNOX Model #G50UH-48C-110 Serial #5907C21488, replaced seized blower motor and wheel that was coming apart from center vanes. Also found one of the motor mounts was broke, replaced motor with new mount, wheel and new run capacitor, tested heating and cooling and system Is operting properly now. i found there is a burn mark on indoor control board, system is operting normally however at this time.
Arrived at customer expressed his concerns to me PVC drain was slightly off the roof and some branches were near the AC unit cleared the branches really a lined PVC drain checked unit to make sure power surge did not affect package unit system is operational at this time perform today as customer courtesy
Kitchen furnace LENNOX Model #G50UH-48C-110 Serial #5907C21488. I found indoor blower wheel is seized and blower wheel is coming apart. Blower motor and wheel both need replaced, 2007 unit and would be a good idea to consider whole unit replacement at this time. I can’t check pressures until repair is made.
Performed maintenance on 1 Lennox gas pack and 1 Goodman heatpump. Checked return and supply temperatures and static pressures, checked compressor operations and refrigerant pressures, checked compressor amps and outdoor motor amps and indoor motor amps, checked capacitors and tightened all electrical components, checked burners and flames and safety switches,
Inspected 2007 Trane php outdoor coil on all sides and hail guard for hail damage, coil and exterior of system are in good shape, no damage. I offered to perform full heating and cooling inspection, Jeff said he does not want me to and the system is already maintained bi-annually.
Completed fall pcp on one trane heat pump system. Checked electrical connections and components. Tightened connections as needed. Checked indoor and outdoor fan motors and coils. Checked filter clean and new. Checked r frigerqnt charge. Super heat and sub cooling. Checked temp rise and static pressure. Noticed the contactor is starting to pit will require replacement with in the next few years. Also noticed the water heated is almost 11 years old
Completed services split heat pump system. Cycle system on heating and checked refrigerant pressure, electrical, motors bearing, amp draws, run caps, coils, temperature split and defrost operational. Found system is operational ok at this time. Thank You For Choosing Hobaica Services.
Check out wine cellar refrigeration system for high humidity issue.
Performed a service call on a Lennox gas pack system. Made wiring adjustment to unit. The system is now cooling properly. Thank you for choosing Hobaica services. Have a great day.
Perform diagnostic on gas split system. Find condensate drain line is clogged. Clean out drain line upon customer approve.
I found water leak in 1/2 inch copper for recirculating line behind wall behind water heater. Took out small square of saturated drywall. We need to uninstall 40 G gas wh to access behind for repair. I shut off hot water To stop leaking and turned off gas valve. Wh is draining with customers hose so it’ll be faster when we come back. I loosened hot water connection on top of wh for it to drain better. I Waived service call fee due to having to shut off Hot water overnight and not fixing the le
Under nww replaced bad compressor and burnt up wiring harness, recover old 410a and evacuated system to 350 microns after welding in new compressor and filter drier, pressure tested and leak checked and recharged by pressures with new 7 lbs R410a and tested cooling. At arrival customer reports indoor fan also stopped working, I Found thermostat LENNOX Model #104515-01Serial #A215H01518 would not bring on just indoor fan, it will during call to cool, then it started working again. We will
2013 Trane php Serial 131511736L 3 ton 3 phase compressor is shorted to ground and needs replaced with 8 lbs r410a and new liquid line filter. Due to compressor burn out there is possibility of acid left behind in system and I recomnnded system replacement vs compressor repair. Stu said he has been customer over 20 years and knows Paul H well, he said he would like to continue to be billed as he always has for service, his office Is closed now until Monday and we will need To bill $99 due.
Performed diagnostic on no cool for suite #100, found blower motor not operating. I checked the VFD controller found it flashing a code of fault 9 / motor overheated. I checked the motor it was cold they said it wasn’t operating all day, the office was operating the generator not sure if that had to do with the error code. But I reset the controller once reset motor started operating. Afte
Performed service call on a ruud package heat pump. Inspected system. Gave options or repair vs replacement. Owners set new unit quote appointment. Thank you for choosing Hobaica services. It was a pleasure to meet you both
Performed a service call for a unit not cooling. Inspected the split unit. Relayed my findings and recommendations with owner. Set appointment for unit replacement quote. Thank you for choosing Hobaica services.
Arrived in central Phoenix to perform a service on a York gas package unit. Evaluated operations in cooling. Relayed my findings with owner. Signed up on maintenance plan. Thank you for choosing Hobaica services.
Performed air-conditioning service on three package heatpump system’s. Upon arrival met with owner who stated units are not operating. Inspected systems per concerns and relayed my findings. Received approvals for repairs. After repairs were completed all systems are now functioning correctly. Thank you very much for choosing Hobaica services. Have a great day.